Model No.: r407c
2.OEM is accepted
|Boiling point 101.3KPa(°C)||-43.80|
|Freezing point 101.3KPa (°C)||-|
|Critical temperature (°C)||87.30|
|Critical pressure (MPa)||4.63|
|Appearance||Colorless and clear|
R407C can be used to retrofit existing R22 systems in positive displacement, direct expansion refrigeration, and air conditioning equipment. R407C should not be used in centrifugal chillers or other equipment that uses a flooded evaporator due, to its high temperature glide. Retrofit Procedure 1. Establish baseline performance. Note the oil type in use and any system operating data (if system is operating properly). Check for existing leaks and identify any needed repairs. 2. Recover the existing refrigerant charge (DO NOT vent to atmosphere). Weigh the amount of refrigerant removed. 3. Drain existing oil from the compressor sump, suction line accumulators, etc. Record the amount of oil removed. Add an equivalent amount of OEM recommended POE oil. 4. Recharge the system with the recovered R22 charge and run the system (at least 1 hour) to circulate the new lubricant. 5. Recover the R-22 charge again and check the residual oil content of the lubricant. The amount of the original lubricant in the POE must be less than 5%. 6. Repeat steps 3 to5, as needed, until the required oil purity level is reached. Once the oil flushes are completed, standard maintenance should be conducted (i.e. filter-drier change, leak repairs). 7. Evacuate the system (less than 500 microns) and ensure it maintains a vacuum. If vacuum is lost, it may indicate that leaks are present in the system. 8. Charge system with R407C refrigerant. Remove refrigerant as liquid only from cylinder. The initial charge weight should be approximately 90% of the standard charge for R-22, charging up to 95% if necessary. 9. Adjust TXV set point and/or refrigerant charge to achieve the desired superheat. Low side pressure control settings may also need to be adjusted. 10. Monitor oil level in the compressor. If necessary, adjust oil amount to attain normal operating level (mid-sight glass).
11. Label system clearly, indicating the type and amounts of system refrigerant and oil. Contact us if you need more details on R407c Refrigerant. We are ready to answer your questions on packaging, logistics, certification or any other aspects about R407c、Refrigerant R407C. If these products fail to match your need, please contact us and we would like to provide relevant information.
Product Categories : R407C Refrigerant Gas
Premium Related Products